Natural water from a well / aquafer under the hotel provides
100% free cooling for all the air conditioning without the use of heat-pumps or chillers
Installation of Fan Coils on the Lower ground Floor, Ground Floor, 1st Floor, 3rd Floor, 5th Floor
Made of galvanized steel, thickness 1 mm, with inside thermal insulation (closed cell polyethelene 6 mm thick) and outside anticondensate lining.
Diffuser with intake grille
In prepainted metal sheet in the colour RAL 9003 with hinged intake grille that can be opened for inspection and maintenance of the air filter.
Polypropylene cellular fabric regenerating filter.
The fans have aluminium or plastic material blades directly keyed on the motor with double aspiration and they are dynamically and statically balanced during manufacture in order to have an extremely quiet operation.
BLAC three phase permanent magnet DC brushless sensorless electronic motor controlled with current reconstructed according to a sinusoidal wave by an inverter board single-phase 220-240 V, 50-60 Hz.
Heat exchange coil
It is manufactured from drawn copper tube and the aluminium fins are mechanically bonded onto the tube by an expansion process.The coil has two 1/2 inch BSP internal connections and 1/8 inch BSP air vent and drain.
Condensate collection tray
Made from plastic with an “L”-shape fitted on the inner casing. The outside diameter of the condensate discharge pipe is 15mm.
The Carisma Coanda one-way cassette units are fitted with round diffusers suitably designed to generate an airflow with “coanda” effect. The direction of diffuser outflow can be changed on site.
One way cassette fan coil unit. The unit is suitable for installation in a suspended ceiling.
Exposed fan coil unit with centrifugal fan. The board is mounted on the unit, closed to the motor, without the need to be cooled down by the air flow.
Circular exhaust valve with attenuation. A manually adjusted supply valve in ceiling installation.
Grille with adjustable horizontal and rear vanes suitable for supply and exhaust.